Ordering: Specify figure number, pipe size, height to center of pipe, and finish. View Data Sheet
Search Results for ""
Size: 1/2” or 3/4” mounting holes. Braces up to 8” Pipe MAX Install: Attach to the structural surface as noted in NFPA13 fastener tables. Please note that the two outermost bolt holes must be used and the middle bolt hole should be used only in conjunction with both outermost bolt holes to ensure concentric loading.
Size: 1/2” mounting hole. Braces up to 8” Pipe MAX Install: Mount device to structure then insert brace element into fitting against back of jaw. Tighten set screw finger tight, then tighten until hex head breaks off. Adjust attachment to proper brace angle. Approvals: Underwriters Laboratories listed for US and Canada and Factory Mutual approved.
Size: Braces up to 8” Pipe MAX. Attaches to 3/8” thick MAX structural members. When attaching to a structure thicker than 3/8”, please see PHD Manufacturing Fig. 045. Install: Steel bar joist manufacturer’s warranty requires attachment within 6” of chord panel point. Place on structural member with the flange contacting the back of the jaw.
Size: Braces up to 8” Pipe MAX. Attaches to 3/8” MINIMUM and 11/4” MAX thick structural members. When attaching to a structure less than 3/8” thick, please see PHD Manufacturing Fig. 035. Install: Place on structural member with the flange contacting the back of the jaw. Tighten set screws finger tight, then evenly tighten until
Size: Pipe sizes 2” thru 8”. Can use 1” thru 2” SCH 40 pipe, structural steel, and PHD 12 gauge strut channel (1001 & 1201) as sway bracing elements. Install: Place attachment around pipe to be braced, positioning brace attachment as needed, then tighten clamping bolts and nuts finger tight. Insert brace component into fitting